Delivery date: 10 days
The solution is an Autotransformer.
By leaving the neutral of the split phase supply unused, and connecting an Autotransformer to create a new neutral, as shown in figure 1, any load unbalance is ‘absorbed’ by the Autotransformer. In case of a 30A supply, the load can be increased to 7,2kVA, and a 20A load unbalance will result in one leg supplying 40A, and the other leg 20A. The 20A difference will flow through the neutral and the windings of the Autotransformer. The current through both 120V wires of the split phase supply will be 30A.
Data Sheet - click here
Latest viewed products
You must add at least one product to compare products.
Was added to wishlist!
Was removed from wishlist!